Contents (2000 - 557)Skip to content
Environmental Planning and Assessment Regulation 2000
Historical version for 15 July 2001 to 13 December 2001 (accessed 27 January 2020 at 01:45) Current version
168 Fire safety schedules
(cf clause 80C of EP&A Regulation 1994)
(1) When:(a) granting a development consent for a change of building use (other than a complying development certificate) in circumstances in which no building work is proposed by the applicant for the consent and no building work is required by the consent authority, or(b) issuing a complying development certificate for the erection of a building or for a change of building use, or(c) issuing a construction certificate for proposed building work, orthe person doing so must issue a schedule (a fire safety schedule) specifying the fire safety measures (both current and proposed) that should be implemented in the building premises.(d) giving a fire safety order in relation to building premises,(2) In the case of a fire safety order in respect of which a further order is made under section 121R of the Act, the fire safety schedule is to be issued when the further order is given.(3) A fire safety schedule:(a) must deal with the whole of the building, not merely the part of the building to which the development consent, complying development certificate, construction certificate or fire safety order relates, and(b) must include:(i) such of the fire safety measures currently implemented in the building premises, andas are statutory fire safety measures, and(ii) such of the fire safety measures proposed or required to be implemented in the building premises,(c) must distinguish between:(i) the fire safety measures currently implemented in the building premises, and(ii) the fire safety measures proposed or required to be implemented in the building premises, and(d) must identify each measure that is a critical fire safety measure and the intervals (being intervals of less than 12 months) at which supplementary fire safety statements must be given to the council in respect of each such measure, and(e) must specify the minimum standard of performance for each fire safety measure included in the schedule.(4) A copy of the fire safety schedule must be attached to (and is taken to form part of) the relevant development consent, complying development certificate, construction certificate or fire safety order and for the purposes of an appeal forms part of the development consent or construction certificate.(5) An earlier fire safety schedule is superseded by a later fire safety schedule, and ceases to have effect when the later fire safety schedule is issued.